ALUMICONN INSTALLATION INSTRUCTIONS
There are 2 sets of Alumiconn installation instructions. The first set of instructions is to be used if you have a torque screwdriver. This method is UL listed. The second set of instructions are to be used if you only have a regular screwdriver. This set of instructions isn’t part of the UL listing, but the manufacturer (King Innovation) stands firmly behind this installation method.
Option 2 – MANUFACTURER APPROVED INSTALLATION INSTRUCTIONS
IMPORTANT: Turn off power before installing or removing connector. Product to be used in accordance with local and national codes.
- Strip conductors 5/16"
- Insert conductor into wire port, fully seating conductor into port.
- This step is manufacturer-approved and is for use on solid wire only. Using a screwdriver, tighten set screw until it comes into contact with the solid conductor. Note location of screwdriver slot and continue tightening the set screw as indicated below.
|Number of Turns||Wire Size / Metal Type|
|1 Full Turn||# 12-10 Solid Aluminum|
|1/2 Turn||# 18-10 Solid Copper|
EXAMPLE OF A TYPICAL APPLICATION
Note: AL = Aluminum, CU = Copper. Also note that the 'power out' is optional and not always applicable, depending on how your wiring is set up.